Instrumental system to estimate the turbuce ratio of the air flow in a rigid grid, based on its reduced dynamic order transfer functions matrix
Keywords:Vibrational modal model, Laminar and turbulent air flow, Reduce order transfer functions matrix.
In words of the cooling technology experts, there is at least a 20-year gap between the nowadays vapor compression based technology for refrigeration, cooling and HVAC, and what we have defined as alternatives technologies. There is also a big amount of scientific effort to endow this vapor compression technology with more degrees of freedom to implement more accurate energy optimization algorithms. In this way, as a first step to get more robust control algorithms in heat interchangers of condenser and evaporators units, authors have developed some instrumentation systems to analyze the behavior of the air flowing through the rigid blades of this kind of devices. This previous effort has been before reported as a complete vibrational modal model for the concerned rigid grid, however; due to its 16 spatially degrees of freedom and its 16th dynamic order, its model re-solution on line while the heat interchanger unit is working is almost impossible with a normal computer. Therefore, to get an algorithm with less computational resource consumption and with the same accuracy than the complete modal model, authors have reported in this document, the implementation of a reduced dynamical order transfer function matrix model. Reduction that as well as it is described is based on the poles averaging and zeros selection, from the set experimental graphs of the frequency spectral magnitude from a set of impact tests (experimental modal testing) performed at LaNITeF-CIDESI. Numerical prediction of the transfer function matrix from the dynamic reduced order model have been validated with the experimental spectral. Based on the hypothesis, that due to the incident angle, the resonance spectral vibration is excited by the laminar air flow, while the air flow turbulence does not excite the resonance vibrational spectral, the turbulence ration from the incident air flow has been analyzed from a wind tunnel test. As the main conclusion, authors have developed and validated a new instrumentation system to analyze the turbulence ratio of the air flow incident in a rigid grid, which can be part of a condenser or evaporator unit from a conventional cooling system, by implementing the concerned transfer functions matrix model with reduced dynamic order.
M. Ponmurugan, M. Ravikumar, and A. Sundaramahalingam, “A review on utilization of waste heat from domestic refrigerator,” Int. Conf. Mater. Manuf. Mach. 2019, vol. 2128, no. May 2015, p. 050015, 2019. https://doi.org/10.1063/1.5117987
Global electricity prices in 2018, by selected country (in U.S. dollars per kilowatt hour). https://www.statista.com/statistics/263263/electricity-prices-in-selected-countries/.
G. D. Librado, L. Alvaro, M. Santiyanes, and H. G. Cuatzin, “Dynamic Behavior Model for Cooling System Based on Vapor Compression Experimental Analysis and Simulation Validation Grounded on a Reduced Order Differential Equation with Few Degrees of Freedom,” in ICONS 2018: The Thirteenth International Conference on Systems, 2018, no. c, pp. 57–62. https://www.thinkmind.org/download.php?articleid=icons_2018_4_20_48003
K. Talukdar, “Modeling of Solar Photovoltaic Assisted Vapor Absorption Refrigeration System for Running an Ice Factory,” IOSR J. Mech. Civ. Eng., vol. 14, no. 03, pp. 60–69, 2017. https://doi.org/10.9790/1684-1403016069
The Vapor Compression Refriferation Cycle, Step by Step, Araner, February 2018, https://www.araner.com/blog/vapor-compression-refrigeration-cycle/
M. Ahmad, A. Bontemps, H. Sallée, and D. Quenard, “Thermal testing and numerical simulation of a prototype cell using light wallboards coupling vacuum isolation panels and phase change material,” Energy Build., vol. 38, no. 6, pp. 673–681, 2006. https://doi.org/10.1016/j.enbuild.2005.11.002
H. Binici, O. Aksogan, M. N. Bodur, E. Akca, and S. Kapur, “Thermal isolation and mechanical properties of fibre reinforced mud bricks as wall materials,” Constr. Build. Mater., vol. 21, no. 4, pp. 901–906, 2007. https://doi.org/10.1016/j.conbuildmat.2005.11.004
S. L. Garrett, J. A. Adeff, T. J. Hofler, S. L. Garrett, J. A. Adeff, and T. J. Hoflers, “Thermoacoustics refrigerator for space application,” J. Thermophys. Heat Transf., vol. 7, no. 4, pp. 595–599, 1993. https://doi.org/10.2514/3.466
P. Gorria, J. L. Sánchez Llamazares, P. Álvarez, M. J. Pérez, J. Sánchez Marcos, and J. A. Blanco, “Relative cooling power enhancement in magneto-caloric nanostructured Pr2Fe17,” J. Phys. D. Appl. Phys., vol. 41, no. 19, pp. 1–5, 2008. https://doi.org/10.1088/0022-3727/41/19/192003
T. Moulton and G. K. Ananthasuresh, “Micromechanical devices with embedded electro-thermal-compliant actuation,” Sensors Actuators, A Phys., vol. 90, no. 1–2, pp. 38–48, 2001. https://doi.org/10.1016/S0924-4247(00)00563-X.
M. S. Layton and J. O’Hagan, Comparison of Alternate Cooling Technologies for California Power Plants:Economic, Environmental and Other Tradeoffs, 1st ed., vol. 2. Sacramento, California, 2002. http://large.stanford.edu/courses/2018/ph241/duboc2/docs/AR-1167.pdf.
2do Seminario Internacional del LaNITeF 2017, Publicaciones del Laboratorio Nacional de Investigación en Tecnologías del Frio, ISBN: 2594-2142X, Vol. 1, No. 2, 2017. https://www.cidesi.com/lanitef/index.html.
M. Sakawa and T. Matsui, “Heat load prediction in district heating and cooling systems through recurrent neural networks,” Int. J. Oper. Res., vol. 23, no. 3, pp. 284–300, 2015. https://doi.org/10.1504/IJOR.2015.069623
A. Marwanto and S. Alifah, “Control of Air Cooling System Based on Fuzzy Logic,” J. Telemat. Informatics, vol. 6, no. 1, pp. 63–70, 2018. https://doi.org/10.12928/jti.v6i1.
E. E. Rodríguez-Vázquez, “Revista Internacional de Investigación e Innovación Tecnológica,” Rev. Int. Investig. e Innovación Tecnológica, vol. 5, no. 30, pp. 1–9, 2018. https://doi.org/10.19053/20278306.v9.n2.2019.9154
M. Stadler, W. Krause, M. Sonnenschein, and U. Vogel, “Modelling and evaluation of control schemes for enhancing load shift of electricity demand for cooling devices,” Environ. Model. Softw., vol. 24, no. 2, pp. 285–295, 2009. https://doi.org/10.1016/j.envsoft.2008.07.003.
H. J. Zúñiga, E. E. Rodríguez, L. A. Montoya, I. Mejia, C. Sandoval, “Vibrational modal model for a compressor blade,” Rev. Int. Investig. e Innovación Tecnológica, vol. 7, no. 41, pp. 1–17, 2019. https://riiit.com.mx/apps/site/idem.php?module=Catalog&action=ViewItem&id=5039&item_id=85353&id=5039.
G. Xu, J. Zhou, H. Geng, M. Lu, and W. Cheng, “Unbalance response analysis of the circumferential tie-rod combined rotor considering different support,” in 2014 IEEE International Conference on Mechatronics and Automation, 2014, pp. 1323–1328. https://doi.org/10.1109/ICMA.2014.6885891
A. Saxena, M. Chouksey, and A. Parey, “Effect of mesh stiffness of healthy and cracked gear tooth on modal and frequency response characteristics of geared rotor system,” Mech. Mach. Theory, vol. 107, no. September 2016, pp. 261–273, 2017. https://doi.org/10.1016/j.mechmachtheory.2016.10.006
B. Hu and H. Gharavi, “A Fast-Recursive Algorithm for Spectrum Tracking in Power Grid Systems,” IEEE Trans. Smart Grid, vol. 10, p. 10.1109/TSG.2018.2813881, 2018. https://doi.org/10.1109/TSG.2018.2813881.
How to Cite
Copyright (c) 2020 Ana Marell Arteaga Martínez, Eloy Edmundo Rodríguez Vázquez, María Elizabeth Rodríguez Ibarra, Helen Janeth Zúñiga Osorio, Luis Álvaro Montoya Santiyanes
This work is licensed under a Creative Commons Attribution 4.0 International License.
The authors who publish in this journal accept the following conditions:
The authors retain the copyright and assign to the journal the right of the first publication, with the work registered with the Creative Commons Attribution license 4.0, which allows third parties to use what is published as long as they mention the authorship of the work and the first publication in this magazine.
Authors may make other independent and additional contractual agreements for the non-exclusive distribution of the version of the article published in this journal (eg, include it in an institutional repository or publish it in a book) as long as they clearly indicate that the work it was first published in this magazine.
Authors are allowed and encouraged to share their work online (for example: in institutional repositories or personal web pages) before and during the manuscript submission process, as it can lead to productive exchanges, greater and more quick citation of published work (see The Effect of Open Access).